Question about RCD
Hello, there is a 50 A difavtomat in the shield and just a 50 A automaton, then a wire comes into the apartment, a 32 A 100 mA difavtomat immediately stands. Then it goes to the machines 10 A (light), 16 A (sockets), 25 A (stove) and 16 A (bathroom). After this, the last machine goes to the RCD 16 A 30 mA. From it care to the outlet (washer) in the bathroom, and light. What became embarrassing. 2.5 squares go to the outlet, but 1.5 squares to the light, stretch ceiling. As I understand it, if the light burns not just to shine but burn, then the wire will burn faster than the 16 A will work? Then put on a 10 A machine? But then the question is: will not cut down the machine? Washer A class! 50W LED light.
Or, in general, put immediately an RCD on the entire electrician after the difavtomat? But then how much Amperes to take UZO ???? Buying a new one is not a problem. And then put the light in the bathroom into the general light. Or is it necessary to put an automatic machine after a difavtomat, then only an RCD, and only then on all automatic machines?