Question about connecting Wekrel walk-through switches with backlight
- The incoming phase is fed to the middle contact of one of the switches, the phase going to the lamp is connected to the middle contact of the second switch. Paired "output" contacts of the switches are interconnected.
- Phase and zero are connected to two “output” contacts of each of the switches, and a lamp is connected between the middle contacts of the switch.
It is necessary to assemble according to the first scheme, and then everything should work as it should. But this is provided that the backlight is connected between the output contacts of the switches, it also happens that the backlight is installed between the output and middle contacts. Where on your “Verkel” I don’t know, I couldn’t find the responsible information, I personally did not work with them.